Modbus TCP/IP Client (Universal and Advanced Models)
The EcoStruxure Panel Server acts as both a Modbus TCP/IP gateway and a Modbus device by using the internal Modbus TCP server.
To correctly configure your Modbus TCP/IP client to access data from Panel Server and from devices under Panel Server , see Modbus Gateway Function.
The Panel Server acts as a Modbus gateway for wired or wireless Ethernet communications from an upstream PC to Ethernet devices and field devices on the downstream network. By using a local monitoring software you can access information from devices for data collection and other functions.
The Panel Server manages Modbus communication on all interfaces including Wi-Fi.
This function is available on Panel Server Universal and Advanced .
Setting the Parameters
IMPAIRED NETWORK PERFORMANCE
Only qualified personnel should modify the Modbus TCP/IP settings. Perform such modifications only after you have read about and understood the Modbus TCP/IP settings.
Failure to follow these instructions can result in loss of network connectivity.
With EcoStruxure Power Commission (EPC) software
On the EcoStruxure Panel Server webpages, at .
For information about the Modbus registers, see the guide of each Modbus-SL device and DOCA0241EN EcoStruxure Panel Server - Modbus File for wireless devices.
Modbus TCP/IP Client Settings
The following table describes the settings and where they are available.
Connection timeout (s)
Used to set the length of time the Panel Server will wait for a remote Modbus TCP/IP device to establish the connection with the Panel Server .
Values from 0.1 to 10 seconds (default setting: 2 seconds)
Message timeout (s)
Used to set the length of time the Panel Server will wait for a remote Modbus TCP/IP device to respond and send a message following a Modbus TCP/IP request initiated by the Panel Server .
Values from 1 to 20 seconds (default setting: 3 seconds)