- Only for dual mains: Add the labels for SSIB, the indicator lights, and the diagram label on the maintenance bypass cabinet. The labels are provided with this manual.
- Add label 885-91965 (provided with the UPS) on the maintenance bypass cabinet.
- Only for seismic anchoring: Install the seismic front anchoring bracket on the maintenance bypass cabinet and on the UPS. Mount the seismic front brackets to the floor. Use appropriate hardware for the floor type – the hole diameter in the seismic front bracket is ø14 mm. The minimum requirement is M12 strength grade 8.8 hardware.
- Close the front door on the maintenance bypass cabinet