Connect the Signal Cables for Single System
- Connect the Class 2/SELV signal cables for the breaker indicator lights from the control terminal block in
the maintenance bypass panel to the UPS as per your configuration.NOTE: The breaker indicator light circuit is considered Class 2/SELV. Class 2/SELV circuits must be isolated from the primary circuitry. Do not connect any circuit to the breaker indicator light terminals unless it can be confirmed that the circuit is Class 2/SELV.
- Connect the non-Class 2/non-SELV signal cables from the control terminal block in the maintenance bypass panel to the UPS as per your configuration.
- Pull up the slack in the signal cables and fasten the signal cables to the cable reliefs.