||Enabled or Disabled
||Specifies if HS Transient capture is enabled.
||Ve or Vn
||Determines the voltage reference. Set the voltage reference
to match your system configuration.
|Magnitude Threshold (VRMS)
||120 - 7100
||Specifies the absolute voltage threshold that must be exceeded
to trigger a HS transient capture. Note that this value is entered
in RMS volts
|Duration Threshold (μs)
||0 - 250.0
||Specifies the length of time that the magnitude threshold must
be exceeded to trigger a HS transient capture. If this register is
set to zero, any voltage that exceeds the magnitude threshold will
trigger a HS transient capture.
||None, Info Only, Low, Medium, High
||Select the alarm priority you want to associate with the HS
transient alarms. To stop an alarm from being displayed without affecting
other meter features, set the alarm priority to Info Only.
||0 - 255
||Select custom priority to view and configure the priority associated
with the alarm. The event log cutoff value is displayed for reference.
Event priorities above the cutoff are stored in the meter’s