Configuring the alarm / energy pulsing LED or digital output for energy pulsing using ION Setup
- Start ION Setup.
- Connect to your meter.
- Navigate to .
- Select the LED or a digital output to configure and click Edit.
The setup screen is displayed.
- Enter a descriptive name for the digital output’s Label.
- Configure the other setup parameters as required.
- Click Send to save your changes.
Alarm / energy pulsing LED setup parameters available through ION Setup
LED: Disabled, Alarm, Energy
Digital output: External, Energy
LED is disabled.
Alarm sets the LED for alarm notification.
Energy sets the LED for energy pulsing.
Energy: associates the digital output with energy pulsing.
External: disassociates the digital output from energy pulsing.
Pulse rate (p/k_h)
1 to 9999999
When configured for energy pulsing, this defines how many pulses are sent to the LED for every 1 kWh, 1 kVARh or 1 kVAh of accumulated energy.
Active Energy Delivered
Active Energy Received
Active Energy Del+Rec
Reactive Energy Delivered
Reactive Energy Received
Reactive Energy Del+Rec
Apparent Energy Delivered
Apparent Energy Received
Apparent Energy Del+Rec
Select which accumulated energy channel to monitor and use for energy pulsing.