Configuring data logging using ION Setup
Changing the meter’s data recorder configuration clears existing data in that data recorder.
Ensure that all important data has been recorded before configuring data recording.
Failure to follow these instructions can result in data loss.
NOTE: The Sg/Sw Buffer Log uses a wizard.
NOTE: EN50160 Logs and IEC 4-30 Logs and System Resources — the amount of memory used by system resources in the meter) are read-only and cannot be configured using Setup Assistant.
- Start ION Setup.
- Open the Setup Assistant for your meter.
- Navigate to .
- In the Status tab, select the data
log and click Edit.The Log Depth Setup window appears.
- Configure the settings as applicable:
Parameter Description Log Interval How frequently records are logged Log Depth Maximum number of records stored in the log Log Memory Information only. This is automatically calculated, and displays how much memory the log uses based on the Log Interval and Log Depth Log Storage Information only. This is automatically calculated, and displays how much total memory is left after subtracting the Log Memory usage