Use Conductor properties to modify the conductor impedances used
in the Voltage Drop and Fault Calculation.
To access the Conductor Properties menu, right-click a conductor
in the Secondary Circuit Analysis window and select Properties from
the resulting menu.
Here you can modify the conductor type and length to automatically
recompute the impedance values. Uncheck the AutoCompute Impedances
checkbox to modify resistance values for impedance.
NOTE: Secondary Circuit Analysis does not carry or
recognize phase information on conductors. The number of phases on
a conductor is determined by its transformer. This is true even if
the conductor is imported from GIS and has GIS attributes indicating
phase information or if conductor phasing information is present in
the description field of the conductor lookup tables. Secondary Circuit
Analysis ignores ALL phase information on a conductor and allows the
transformer phases to imply the phases for the circuit.