The ION meter and DLMS communications
The values available by default are outlined in “Default COSEM objects”.
ION architecture and DLMS
The modules used in the ION meter implementation are:
Event Log Controller module
Data Recorder modules
DLMS Log Export module
See the ION Reference for detailed information on module settings and operation.
The value of the Profile
Generic attribute for
recording interval (attribute
4) is determined by the Record input of the Data
Recorder linked to the DLMS Log Export module:
If the Record input is linked to a Periodic Timer module, the value of the Period setup register for that Periodic Timer module is reported as the recording interval for attribute 4.
If the Record input is not linked to a Periodic Timer module, the recording interval is reported as 0.
Configuring meter communications
You need to configure the meter’s communication settings before you can access values using DLMS master software.
Use the front panel or ION Setup to set the Protocol for the communication port you want to use to DLMS.
See your meter’s user manual for detailed instructions on configuring communications.