Install Busbars Between the UPS and the Maintenance Bypass Cabinet in Dual Mains System
The busbars and insulator parts are provided in a kit with the maintenance bypass cabinet. The part numbers shown on the illustrations are printed on the parts. Use the provided M8x30 screws and torque to 17.5 Nm (12.91 lb-ft / 154.9 lb-in).
- Remove the three single mains busbars.
- Install the input busbars, the neutral busbar, the DC busbars, the insulator part, and the ground busbar.
- Install the bypass busbars and the insulator part.
- Install the output busbars and the insulator parts.