Configure the Output
- Tap .
- Set the AC voltage ph-ph to 380VAC, 400VAC, 415VAC, 440VAC, or 480VAC depending on your configuration.
- Set the Frequency to 50Hz ±1.0, 50Hz ±3.0, 50Hz ±10.0, 60Hz ±1.0, 60Hz ±3.0, or 60Hz ±10.0 depending on your configuration.
- Tap OK to save your settings and tap the arrow symbol to go to the next page.
- Set the Bypass and output tolerance (%). The bypass and output tolerance range is +3% to +10%, default is +10%.
- Set the Voltage compensation (%). The output voltage of the UPS can be adjusted up to ±3% to compensate for different cable lengths. Default is 0%.
- Set the Overload threshold (%). The overload range is 0% to 100%, default is 75%.
- Set the Transformer voltage compensation (%). The transformer voltage compensation range is 0% to 3%, default is 0%. See Output Transformer Voltage Compensation for more details and Configure the UPS Input for configuring that an output transformer is present.
- Tap OK to save your settings.