NOTE: The neutral jumper makes a bolted connection of the neutral so that the neutral is
not disconnected when the 4-pole breakers are opened.
NOTE: Only remove the neutral jumpers in a Galaxy VS installation, if this is a local requirement.
Removal of the neutral jumpers is an option for a Galaxy VS installation.
NOTE: Always remove the neutral jumpers in an Easy UPS 3S installation or in an Easy UPS
3M installation. Removal of the neutral jumpers is mandatory for an Easy UPS 3S or an Easy UPS 3M installation.