Specifications
Specifications for 200 kW UPS
Voltage (V)  380  400  415  440  480  

Input  Connections  Single mains: 4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) Dual mains: 3wire (L1, L2, L3, PE) 
Single mains: 4wire* (L1, L2, L3, N, G) or 3wire* (L1, L2, L3, G) Dual mains: 3wire* (L1, L2, L3, G) 

Input voltage range (V)  331437  340460  353477  374506  408552  
Frequency (Hz)  4070  
Nominal input current (A)  316  299  288  272  249  
Maximum input current (A)  364  359  346  326  298  
Input current limitation (A)  364  364  360  336  308  
Total harmonic distortion (THDI)  <3% at 100% load  
Input power factor  >0.99 at load >25%, 0.95 at >15% load  
Protection  Builtin backfeed protection and fuses  
Rampin  Adaptive 1300 seconds  
Bypass  Connections  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G) 

Bypass voltage range (V)  342418  360440  374457  396484  432528  
Frequency (Hz)  50 or 60  
Frequency range (Hz)  Programmable: ±1, ±3, ±10. Default is ±3.  
Nominal bypass current (A)  307  292  281  265  243  
Maximum input short circuit level (three cycles)  65 kA Icw 25 kA Icw with maintenance bypass cabinet 45 kA Icw with bottom entry cabinet 45 kA Icc with backfeed breaker kit installed in the UPS 
65 kAIC 65 kAIC with maintenance bypass cabinet 45 kAIC with bottom entry cabinet 45 kAIC with backfeed breaker kit installed in the UPS 

I^{2}t thyristor value (A^{2}s)  3.1 MA^{2}s  
Bypass backfeed protection options  1: Upstream installation of breaker with shunt trip connected to the UPS, OR 2: Installation with maintenance bypass cabinet, OR 3: Installation of backfeed breaker kit in the UPS. 

Output  Connections*  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G, GEC*) 

Output voltage regulation  Symmetrical load ± 1% Asymmetrical load ± 3% 

Overload capacity  Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 

Dynamic load response  ± 5% after 2 ms, ± 1% after 50 ms  
Output power factor  1  
Nominal output current (A)  304  289  278  262  241  
Output frequency (Hz)  50/60 (synchronized to bypass), 50/60 Hz ±0.1% (freerunning)  
Synchronized slew rate (Hz/sec)  Programmable: 0.25, 0.5, 1, 2, 4, 6  
Total harmonic distortion (THDU)  <1% for linear load, <5% for nonlinear load  
Output performance classification (according to IEC/ EN620403)  VFISS111  
Load crest factor  3  
Load power factor  0.5 leading to 0.5 lagging without derating  
Battery  Charging power in % of output power  040% load: 80% 100% load: 15% 
040% load: 80% 100% load: 20% 

Maximum charging power (kW)  040% load: 160 100% load: 30 
040% load: 160 100% load: 40 

Nominal battery voltage (VDC)  480 for 40 blocks 576 for 48 blocks 

Nominal float voltage (VDC)  545 for 40 blocks 654 for 48 blocks 

Maximum boost voltage (VDC)  571 for 40 blocks 685 for 48 blocks 

Temperature compensation (per cell)  3.3mV/°C for T ≥ 25 °C, 0mV/°C for T < 25 °C  
End of discharge voltage (full load) (VDC)  384  
End of discharge voltage (no load) (VDC)  420  
Battery current at full load and nominal battery voltage (A)  434  
Battery current at full load and minimum battery voltage (A)  543  
Ripple current  < 5% C20 (5 minute runtime)  
Battery test  Manual/automatic (selectable)  
Maximum short circuit rating  30 kA 
Specifications for 250 kW UPS
Voltage (V)  380  400  415  440  480  

Input  Connections  Single mains: 4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) Dual mains: 3wire (L1, L2, L3, PE) 
Single mains: 4wire* (L1, L2, L3, N, G) or 3wire* (L1, L2, L3, G) Dual mains: 3wire* (L1, L2, L3, G) 

Input voltage range (V)  331437  340460  353477  374506  408552  
Frequency (Hz)  4070  
Nominal input current (A)  395  374  360  340  311  
Maximum input current (A)  455  449  432  408  373  
Input current limitation (A)  455  455  450  420  385  
Total harmonic distortion (THDI)  <3% at 100% load  
Input power factor  >0.99 at load >25%, 0.95 at >15% load  
Protection  Builtin backfeed protection and fuses  
Rampin  Adaptive 1300 seconds  
Bypass  Connections  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G) 

Bypass voltage range (V)  342418  360440  374457  396484  432528  
Frequency (Hz)  50 or 60  
Frequency range (Hz)  Programmable: ±1, ±3, ±10. Default is ±3.  
Nominal bypass current (A)  384  364  351  331  304  
Maximum input short circuit level (three cycles)  65 kA Icw 25 kA Icw with maintenance bypass cabinet 45 kA Icw with bottom entry cabinet 45 kA Icc with backfeed breaker kit installed in the UPS 
65 kAIC 65 kAIC with maintenance bypass cabinet 45 kAIC with bottom entry cabinet 45 kAIC with backfeed breaker kit installed in the UPS 

I^{2}t thyristor value (A^{2}s)  3.1 MA^{2}s  
Bypass backfeed protection options  1: Upstream installation of breaker with shunt trip connected to the UPS, OR 2: Installation with maintenance bypass cabinet, OR 3: Installation of backfeed breaker kit in the UPS. 

Output  Connections*  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G, GEC*) 

Output voltage regulation  Symmetrical load ± 1% Asymmetrical load ± 3% 

Overload capacity 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 

Dynamic load response  ± 5% after 2 ms, ± 1% after 50 ms  
Output power factor  1  
Nominal output current (A)  380  361  348  328  301  
Output frequency (Hz)  50/60 (synchronized to bypass), 50/60 Hz ±0.1% (freerunning)  
Synchronized slew rate (Hz/sec)  Programmable: 0.25, 0.5, 1, 2, 4, 6  
Total harmonic distortion (THDU)  <1% for linear load, <5% for nonlinear load  
Output performance classification (according to IEC/ EN620403)  VFISS111  
Load crest factor  3  
Load power factor  0.5 leading to 0.5 lagging without derating  
Battery  Charging power in % of output power  040% load: 80% 100% load: 15% 
040% load: 80% 100% load: 20% 

Maximum charging power (kW)  040% load: 200 100% load: 37.5 
040% load: 200 100% load: 50 

Nominal battery voltage (VDC)  480 for 40 blocks 576 for 48 blocks 

Nominal float voltage (VDC)  545 for 40 blocks 654 for 48 blocks 

Maximum boost voltage (VDC)  571 for 40 blocks 685 for 48 blocks 

Temperature compensation (per cell)  3.3mV/°C for T ≥ 25 °C, 0mV/°C for T < 25 °C  
End of discharge voltage (full load) (VDC)  384  
End of discharge voltage (no load) (VDC)  420  
Battery current at full load and nominal battery voltage (A)  543  
Battery current at full load and minimum battery voltage (A)  678  
Ripple current  < 5% C20 (5 minute runtime)  
Battery test  Manual/automatic (selectable)  
Maximum short circuit rating  30 kA 
Specifications for 300 kW UPS
Voltage (V)  380  400  415  440  480  

Input  Connections  Single mains: 4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) Dual mains: 3wire (L1, L2, L3, PE) 
Single mains: 4wire* (L1, L2, L3, N, G) or 3wire* (L1, L2, L3, G) Dual mains: 3wire* (L1, L2, L3, G) 

Input voltage range (V)  331437  340460  353477  374506  408552  
Frequency (Hz)  4070  
Nominal input current (A)  474  449  432  408  373  
Maximum input current (A)  546  539  519  490  447  
Input current limitation (A)  546  546  540  504  462  
Total harmonic distortion (THDI)  <3% at 100% load  
Input power factor  >0.99 at load >25%, 0.95 at >15% load  
Protection  Builtin backfeed protection and fuses  
Rampin  Adaptive 1300 seconds  
Bypass  Connections  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G) 

Bypass voltage range (V)  342418  360440  374457  396484  432528  
Frequency (Hz)  50 or 60  
Frequency range (Hz)  Programmable: ±1, ±3, ±10. Default is ±3.  
Nominal bypass current (A)  460  437  422  398  364  
Maximum input short circuit level (three cycles)  65 kA Icw 25 kA Icw with maintenance bypass cabinet 45 kA Icw with bottom entry cabinet 45 kA Icc with backfeed breaker kit installed in the UPS 
65 kAIC 65 kAIC with maintenance bypass cabinet 45 kAIC with bottom entry cabinet 45 kAIC with backfeed breaker kit installed in the UPS 

I^{2}t thyristor value (A^{2}s)  3.1 MA^{2}s  
Bypass backfeed protection options  1: Upstream installation of breaker with shunt trip connected to the UPS, OR 2: Installation with maintenance bypass cabinet, OR 3: Installation of backfeed breaker kit in the UPS. 

Output  Connections*  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G, GEC*) 

Output voltage regulation  Symmetrical load ± 1% Asymmetrical load ± 3% 

Overload capacity 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 

Dynamic load response  ± 5% after 2 ms, ± 1% after 50 ms  
Output power factor  1  
Nominal output current (A)  456  433  417  394  361  
Output frequency (Hz)  50/60 (synchronized to bypass), 50/60 Hz ±0.1% (freerunning)  
Synchronized slew rate (Hz/sec)  Programmable: 0.25, 0.5, 1, 2, 4, 6  
Total harmonic distortion (THDU)  <1% for linear load, <5% for nonlinear load  
Output performance classification (according to IEC/ EN620403)  VFISS111  
Load crest factor  3  
Load power factor  0.5 leading to 0.5 lagging without derating  
Battery  Charging power in % of output power  040% load: 80% 100% load: 15% 
040% load: 80% 100% load: 20% 

Maximum charging power (kW)  040% load: 240 100% load: 45 
040% load: 240 100% load: 60 

Nominal battery voltage (VDC)  480 for 40 blocks 576 for 48 blocks 

Nominal float voltage (VDC)  545 for 40 blocks 654 for 48 blocks 

Maximum boost voltage (VDC)  571 for 40 blocks 685 for 48 blocks 

Temperature compensation (per cell)  3.3mV/°C for T ≥ 25 °C, 0mV/°C for T < 25 °C  
End of discharge voltage (full load) (VDC)  384  
End of discharge voltage (no load) (VDC)  420  
Battery current at full load and nominal battery voltage (A)  651  
Battery current at full load and minimum battery voltage (A)  814  
Ripple current  < 5% C20 (5 minute runtime)  
Battery test  Manual/automatic (selectable)  
Maximum short circuit rating  30 kA 
Specifications for 350 kW UPS
Voltage (V)  380  400  415  440  480  

Input  Connections  Single mains: 4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) Dual mains: 3wire (L1, L2, L3, PE) 
Single mains: 4wire* (L1, L2, L3, N, G) or 3wire* (L1, L2, L3, G) Dual mains: 3wire* (L1, L2, L3, G) 

Input voltage range (V)  331437  340460  353477  374506  408552  
Frequency (Hz)  4070  
Nominal input current (A)  553  524  505  476  435  
Maximum input current (A)  637  629  605  571  522  
Input current limitation (A)  637  637  630  588  539  
Total harmonic distortion (THDI)  <3% at 100% load  
Input power factor  >0.99 at load >25%, 0.95 at >15% load  
Protection  Builtin backfeed protection and fuses  
Rampin  Adaptive 1300 seconds  
Bypass  Connections  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G) 

Bypass voltage range (V)  342418  360440  374457  396484  432528  
Frequency (Hz)  50 or 60  
Frequency range (Hz)  Programmable: ±1, ±3, ±10. Default is ±3.  
Nominal bypass current (A)  537  510  492  464  425  
Maximum input short circuit level (three cycles)  65 kA Icw 25 kA Icw with maintenance bypass cabinet 45 kA Icw with bottom entry cabinet 45 kA Icc with backfeed breaker kit installed in the UPS 
65 kAIC 65 kAIC with maintenance bypass cabinet 45 kAIC with bottom entry cabinet 45 kAIC with backfeed breaker kit installed in the UPS 

I^{2}t thyristor value (A^{2}s)  3.1 MA^{2}s  
Bypass backfeed protection options  1: Upstream installation of breaker with shunt trip connected to the UPS, OR 2: Installation with maintenance bypass cabinet, OR 3: Installation of backfeed breaker kit in the UPS. 

Output  Connections*  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G, GEC*) 

Output voltage regulation  Symmetrical load ± 1% Asymmetrical load ± 3% 

Overload capacity 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 

Dynamic load response  ± 5% after 2 ms, ± 1% after 50 ms  
Output power factor  1  
Nominal output current (A)  532  505  487  459  421  
Output frequency (Hz)  50/60 (synchronized to bypass), 50/60 Hz ±0.1% (freerunning)  
Synchronized slew rate (Hz/sec)  Programmable: 0.25, 0.5, 1, 2, 4, 6  
Total harmonic distortion (THDU)  <1% for linear load, <5% for nonlinear load  
Output performance classification (according to IEC/ EN620403)  VFISS111  
Load crest factor  3  
Load power factor  0.5 leading to 0.5 lagging without derating  
Battery  Charging power in % of output power  040% load: 80% 100% load: 15% 
040% load: 80% 100% load: 20% 

Maximum charging power (kW)  040% load: 280 100% load: 52.5 
040% load: 280 100% load: 70 

Nominal battery voltage (VDC)  480 for 40 blocks 576 for 48 blocks 

Nominal float voltage (VDC)  545 for 40 blocks 654 for 48 blocks 

Maximum boost voltage (VDC)  571 for 40 blocks 685 for 48 blocks 

Temperature compensation (per cell)  3.3mV/°C for T ≥ 25 °C, 0mV/°C for T < 25 °C  
End of discharge voltage (full load) (VDC)  384  
End of discharge voltage (no load) (VDC)  420  
Battery current at full load and nominal battery voltage (A)  760  
Battery current at full load and minimum battery voltage (A)  949  
Ripple current  < 5% C20 (5 minute runtime)  
Battery test  Manual/automatic (selectable)  
Maximum short circuit rating  30 kA 
Specifications for 400 kW UPS
Voltage (V)  380  400  415  440  480  

Input  Connections  Single mains: 4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) Dual mains: 3wire (L1, L2, L3, PE) 
Single mains: 4wire* (L1, L2, L3, N, G) or 3wire* (L1, L2, L3, G) Dual mains: 3wire* (L1, L2, L3, G) 

Input voltage range (V)  331437  340460  353477  374506  408552  
Frequency (Hz)  4070  
Nominal input current (A)  632  599  577  544  497  
Maximum input current (A)  728  719  692  653  596  
Input current limitation (A)  728  728  720  672  616  
Total harmonic distortion (THDI)  <3% at 100% load  
Input power factor  >0.99 at load >25%, 0.95 at >15% load  
Protection  Builtin backfeed protection and fuses  
Rampin  Adaptive 1300 seconds  
Bypass  Connections  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G) 

Bypass voltage range (V)  342418  360440  374457  396484  432528  
Frequency (Hz)  50 or 60  
Frequency range (Hz)  Programmable: ±1, ±3, ±10. Default is ±3.  
Nominal bypass current (A)  614  583  562  530  486  
Maximum input short circuit level (three cycles)  65 kA Icw 25 kA Icw with maintenance bypass cabinet 45 kA Icw with bottom entry cabinet 45 kA Icc with backfeed breaker kit installed in the UPS 
65 kAIC 65 kAIC with maintenance bypass cabinet 45 kAIC with bottom entry cabinet 45 kAIC with backfeed breaker kit installed in the UPS 

I^{2}t thyristor value (A^{2}s)  3.1 MA^{2}s  
Bypass backfeed protection options  1: Upstream installation of breaker with shunt trip connected to the UPS, OR 2: Installation with maintenance bypass cabinet, OR 3: Installation of backfeed breaker kit in the UPS. 

Output  Connections*  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G, GEC*) 

Output voltage regulation  Symmetrical load ± 1% Asymmetrical load ± 3% 

Overload capacity 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 

Dynamic load response  ± 5% after 2 ms, ± 1% after 50 ms  
Output power factor  1  
Nominal output current (A)  608  577  556  525  481  
Output frequency (Hz)  50/60 (synchronized to bypass), 50/60 Hz ±0.1% (freerunning)  
Synchronized slew rate (Hz/sec)  Programmable: 0.25, 0.5, 1, 2, 4, 6  
Total harmonic distortion (THDU)  <1% for linear load, <5% for nonlinear load  
Output performance classification (according to IEC/ EN620403)  VFISS111  
Load crest factor  3  
Load power factor  0.5 leading to 0.5 lagging without derating  
Battery  Charging power in % of output power  040% load: 80% 100% load: 15% 
040% load: 80% 100% load: 20% 

Maximum charging power (kW)  040% load: 320 100% load: 60 
040% load: 320 100% load: 80 

Nominal battery voltage (VDC)  480 for 40 blocks 576 for 48 blocks 

Nominal float voltage (VDC)  545 for 40 blocks 654 for 48 blocks 

Maximum boost voltage (VDC)  571 for 40 blocks 685 for 48 blocks 

Temperature compensation (per cell)  3.3mV/°C for T ≥ 25 °C, 0mV/°C for T < 25 °C  
End of discharge voltage (full load) (VDC)  384  
End of discharge voltage (no load) (VDC)  420  
Battery current at full load and nominal battery voltage (A)  868  
Battery current at full load and minimum battery voltage (A)  1085  
Ripple current  < 5% C20 (5 minute runtime)  
Battery test  Manual/automatic (selectable)  
Maximum short circuit rating  30 kA 
Specifications for 450 kW UPS
Voltage (V)  380  400  415  440  480  

Input  Connections  Single mains: 4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) Dual mains: 3wire (L1, L2, L3, PE) 
Single mains: 4wire* (L1, L2, L3, N, G) or 3wire* (L1, L2, L3, G) Dual mains: 3wire* (L1, L2, L3, G) 

Input voltage range (V)  331437  340460  353477  374506  408552  
Frequency (Hz)  4070  
Nominal input current (A)  711  674  649  612  559  
Maximum input current (A)  819  809  778  734  671  
Input current limitation (A)  819  819  810  756  693  
Total harmonic distortion (THDI)  <3% at 100% load  
Input power factor  >0.99 at load >25%, 0.95 at >15% load  
Protection  Builtin backfeed protection and fuses  
Rampin  Adaptive 1300 seconds  
Bypass  Connections  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G) 

Bypass voltage range (V)  342418  360440  374457  396484  432528  
Frequency (Hz)  50 or 60  
Frequency range (Hz)  Programmable: ±1, ±3, ±10. Default is ±3.  
Nominal bypass current (A)  691  656  632  596  547  
Maximum input short circuit level (three cycles)  65 kA Icw 25 kA Icw with maintenance bypass cabinet 45 kA Icw with bottom entry cabinet 45 kA Icc with backfeed breaker kit installed in the UPS 
65 kAIC 65 kAIC with maintenance bypass cabinet 45 kAIC with bottom entry cabinet 45 kAIC with backfeed breaker kit installed in the UPS 

I^{2}t thyristor value (A^{2}s)  3.1 MA^{2}s  
Bypass backfeed protection options  1: Upstream installation of breaker with shunt trip connected to the UPS, OR 2: Installation with maintenance bypass cabinet, OR 3: Installation of backfeed breaker kit in the UPS. 

Output  Connections*  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G, GEC*) 

Output voltage regulation  Symmetrical load ± 1% Asymmetrical load ± 3% 

Overload capacity 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 

Dynamic load response  ± 5% after 2 ms, ± 1% after 50 ms  
Output power factor  1  
Nominal output current (A)  684  650  626  590  541  
Output frequency (Hz)  50/60 (synchronized to bypass), 50/60 Hz ±0.1% (freerunning)  
Synchronized slew rate (Hz/sec)  Programmable: 0.25, 0.5, 1, 2, 4, 6  
Total harmonic distortion (THDU)  <1% for linear load, <5% for nonlinear load  
Output performance classification (according to IEC/ EN620403)  VFISS111  
Load crest factor  3  
Load power factor  0.5 leading to 0.5 lagging without derating  
Battery  Charging power in % of output power  040% load: 80% 100% load: 15% 
040% load: 80% 100% load: 20% 

Maximum charging power (kW)  040% load: 360 100% load: 67.5 
040% load: 360 100% load: 90 

Nominal battery voltage (VDC)  480 for 40 blocks 576 for 48 blocks 

Nominal float voltage (VDC)  545 for 40 blocks 654 for 48 blocks 

Maximum boost voltage (VDC)  571 for 40 blocks 685 for 48 blocks 

Temperature compensation (per cell)  3.3mV/°C for T ≥ 25 °C, 0mV/°C for T < 25 °C  
End of discharge voltage (full load) (VDC)  384  
End of discharge voltage (no load) (VDC)  420  
Battery current at full load and nominal battery voltage (A)  977  
Battery current at full load and minimum battery voltage (A)  1221  
Ripple current  < 5% C20 (5 minute runtime)  
Battery test  Manual/automatic (selectable)  
Maximum short circuit rating  30 kA 
Specifications for 500 kW UPS
Voltage (V)  380  400  415  440  480  

Input  Connections  Single mains: 4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) Dual mains: 3wire (L1, L2, L3, PE) 
Single mains: 4wire* (L1, L2, L3, N, G) or 3wire* (L1, L2, L3, G) Dual mains: 3wire* (L1, L2, L3, G) 

Input voltage range (V)  331437  340460  353477  374506  408552  
Frequency (Hz)  4070  
Nominal input current (A)  790  749  721  680  621  
Maximum input current (A)  910  898  865  816  746  
Input current limitation (A)  910  910  900  840  770  
Total harmonic distortion (THDI)  <3% at 100% load  
Input power factor  >0.99 at load >25%, 0.95 at >15% load  
Protection  Builtin backfeed protection and fuses  
Rampin  Adaptive 1300 seconds  
Bypass  Connections  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G) 

Bypass voltage range (V)  342418  360440  374457  396484  432528  
Frequency (Hz)  50 or 60  
Frequency range (Hz)  Programmable: ±1, ±3, ±10. Default is ±3.  
Nominal bypass current (A)  767  729  703  663  607  
Maximum input short circuit level (three cycles)  65 kA Icw 25 kA Icw with maintenance bypass cabinet 45 kA Icw with bottom entry cabinet 45 kA Icc with backfeed breaker kit installed in the UPS 
65 kAIC 65 kAIC with maintenance bypass cabinet 45 kAIC with bottom entry cabinet 45 kAIC with backfeed breaker kit installed in the UPS 

I^{2}t thyristor value (A^{2}s)  3.1 MA^{2}s  
Bypass backfeed protection options  1: Upstream installation of breaker with shunt trip connected to the UPS, OR 2: Installation with maintenance bypass cabinet, OR 3: Installation of backfeed breaker kit in the UPS. 

Output  Connections*  4wire (L1, L2, L3, N, PE) or 3wire (L1, L2, L3, PE) 
4wire (L1, L2, L3, N, G) or 3wire (L1, L2, L3, G, GEC*) 

Output voltage regulation  Symmetrical load ± 1% Asymmetrical load ± 3% 

Overload capacity 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 
Normal operation: 150% for 1 minute, 125% for 10 minutes, (110% continuous*) 

Dynamic load response  ± 5% after 2 ms, ± 1% after 50 ms  
Output power factor  1  
Nominal output current (A)  760  722  696  656  601  
Output frequency (Hz)  50/60 (synchronized to bypass), 50/60 Hz ±0.1% (freerunning)  
Synchronized slew rate (Hz/sec)  Programmable: 0.25, 0.5, 1, 2, 4, 6  
Total harmonic distortion (THDU)  <1% for linear load, <5% for nonlinear load  
Output performance classification (according to IEC/ EN620403)  VFISS111  
Load crest factor  3  
Load power factor  0.5 leading to 0.5 lagging without derating  
Battery  Charging power in % of output power  040% load: 80% 100% load: 15% 
040% load: 80% 100% load: 20% 

Maximum charging power (kW)  040% load: 400 100% load: 75 
040% load: 400 100% load: 100 

Nominal battery voltage (VDC)  480 for 40 blocks 576 for 48 blocks 

Nominal float voltage (VDC)  545 for 40 blocks 654 for 48 blocks 

Maximum boost voltage (VDC)  571 for 40 blocks 685 for 48 blocks 

Temperature compensation (per cell)  3.3mV/°C for T ≥ 25 °C, 0mV/°C for T < 25 °C  
End of discharge voltage (full load) (VDC)  384  
End of discharge voltage (no load) (VDC)  420  
Battery current at full load and nominal battery voltage (A)  1085  
Battery current at full load and minimum battery voltage (A)  1356  
Ripple current  < 5% C20 (5 minute runtime)  
Battery test  Manual/automatic (selectable)  
Maximum short circuit rating  30 kA 
Upstream and Downstream Protection for IEC
DANGER 

Hazard of electric shock, explosion, or arc flash
Failure to follow these instructions will result in death or serious injury.

Schneider Electric reserves the right to remove the Live Swap label from the product front if the conditions are not met.
The bypass/output breakers are sized for low grid voltage UN 10%. The battery breakers are sized and trimmed for kW rating at end of discharge voltage but does not necessarily offer overload protection as the cables are sized for kW rating at end of discharge voltage in accordance with IEC 60364 433.3 Omission of devices for protection against overload.
Recommended Upstream Protection for IEC
UPS rating  200 kW  

Input  Bypass/Output  Battery  
Voltage (V)  380  400  415  440  380  400  415  440  380440 
Breaker type 
ComPacT NSX 400H MicroLogic 2.0 (3P: C4032D400, 4P: C4042D400) 
ComPacT NS 630S DC TMD (C634TM630D)  
In/trip unit  400  400  400  400  400  400  400  400  360 
Io  400  360  360  360  360  360  320  320  – 
Ir setting  0.92  1  0.97  0.94  0.95  0.9  0.98  0.93  0.9 
Ir  368  360  349  338  342  324  314  298  567 
Isd  <10 x Ir  <10 x Ir  <10 x Ir  <10 x Ir  10 x Ir  10 x Ir  10 x Ir  10 x Ir  <10 x Ir 
UPS rating  250 kW  

Input  Bypass/Output  Battery  
Voltage (V)  380  400  415  440  380  400  415  440  380440 
Breaker type  ComPacT NSX 630H MicroLogic 2.0 (3P: C6332D630, 4P: C6342D630)  ComPacT NSX 400H MicroLogic 2.0 (3P: C4032D400, 4P: C4042D400) 
MasterPacT NW10HDCD MicroLogic 1.0 DC (48649+65272)  
In/trip unit  630  630  630  630  630  630  400  400  1000 
Io  500  450  450  450  450  450  400  400  – 
Ir setting  0.92  1  0.97  0.94  0.95  0.9  0.98  0.93  – 
Ir  460  450  436  423  428  405  392  372  1000 
Isd  <10 x Ir  <10 x Ir  <10 x Ir  <10 x Ir  10 x Ir  10 x Ir  10 x Ir  10 x Ir  1500 
UPS rating  300 kW  

Input  Bypass/Output  Battery  
Voltage (V)  380  400  415  440  380  400  415  440  380440 
Breaker type  ComPacT NSX 630H MicroLogic 2.0 (3P: C6332D630, 4P: C6342D630)  MasterPacT NW10HDCD MicroLogic 1.0 DC (48649+65272)  
In/trip unit  630  630  630  630  630  630  630  630  1000 
Io  570  570  570  570  570  500  500  450  – 
Ir setting  0.96  0.95  0.92  0.9  0.9  0.98  0.94  1  – 
Ir  547  542  524  513  513  490  470  450  1000 
Isd  <10 x Ir  <10 x Ir  <10 x Ir  <10 x Ir  10 x Ir  10 x Ir  10 x Ir  10 x Ir  <10 x Ir 
UPS rating  350 kW  

Input  Bypass/Output  Battery  
Voltage (V)  380  400  415  440  380  400  415  440  380440 
Breaker type  ComPacT NS800H MicroLogic 5.0 (3P: 33553, 4P: 33556)  ComPacT NSX 630H MicroLogic 2.0 (3P: C6332D630, 4P: C6342D630)  MasterPacT NW10HDCD MicroLogic 1.0 DC (48649+65272)  
In/trip unit  800  630  630  630  630  630  630  630  1000 
Io  –  630  630  630  630  570  570  570  – 
Ir setting  0.8  1  0.97  0.94  0.95  1  0.96  0.92  – 
Ir  640  630  611  592  598  570  547  524  1000 
Isd/ii*  <10 x Ir  <10 x Ir  <10 x Ir  <10 x Ir  10 x Ir  10 x Ir  10 x Ir  10 x Ir  <10 x Ir 
UPS rating  400 kW  

Input  Bypass/Output  Battery  
Voltage (V)  380  400  415  440  380  400  415  440  380440 
Breaker type  ComPacT NS800H MicroLogic 5.0 (3P: 33553, 4P: 33556)  ComPacT NSX 630H MicroLogic 2.0 (3P: C6332D630, 4P: C6342D630) 
MasterPacT NW20HDCD MicroLogic 1.0 DC (48652+65273)  
In/trip unit  800  800  800  800  800  800  630  630  2000 
Io  –  –  –  –  –  –  630  630  – 
Ir setting  0.95  0.9  0.9  0.9  0.9  0.9  1  0.94  – 
Ir  760  720  720  720  720  720  630  592  2000 
Isd/ii*  <10 x In  <10 x In  <10 x In  <10 x In  10 x In  10 x In  10 x Ir  10 x Ir  <10 x Ir 
UPS rating  450 kW  

Input  Bypass/Output  Battery  
Voltage (V)  380  400  415  440  380  400  415  440  380440 
Breaker type  ComPacT NS1000H MicroLogic 5.0 (3P: 33559, 4P: 33562) 
ComPacT NS800H MicroLogic 5.0 (3P: 33553, 4P: 33556) 
ComPacT NS800H MicroLogic 5.0 (3P: 33553, 4P: 33556)  MasterPacT NW20HDCD MicroLogic 1.0 DC (48652+65273)  
In/trip unit  1000  1000  800  800  800  800  800  800  2000 
Io  –  –  –  –  –  –  –  –  – 
Ir setting  0.9  0.9  0.98  0.95  0.98  0.95  0.9  0.9  – 
Ir  900  900  784  760  784  760  720  720  2000 
Isd/ii*  <8 x In  <8 x In  <10 x In  <10 x In  10 x In  10 x In  10 x In  10 x In  2500 
UPS rating  500 kW  

Input  Bypass/Output  Battery  
Voltage (V)  380  400  415  440  380  400  415  440  380440 
Breaker type  ComPacT NS1000H MicroLogic 5.0 (3P: 33559, 4P: 33562)  ComPacT NS800H MicroLogic 5.0 (3P: 33553, 4P: 33556) 
MasterPacT NW20HDCD MicroLogic 1.0 DC (48652+65273)  
In/trip unit  1000  1000  1000  1000  1000  1000  800  800  2000 
Io  –  –  –  –  –  –  –  –  – 
Ir setting  0.95  0.9  0.9  0.9  0.9  0.9  0.98  0.95  – 
Ir  950  900  900  900  900  900  784  760  2000 
Isd/ii*  <8 x In  <8 x In  <8 x In  <8 x In  8 x In  8 x In  10 x In  10 x In  2500 
Recommended Downstream Protection for Distribution Circuit Breakers for IEC
UPS rating  200 kW  250 kW  300 kW  350 kW  400 kW  450 kW  500 kW 

Breaker type  NSX160  NSX250  NSX400  
Trip module type  TMD or Micrologic  TMD or Micrologic  Micrologic  
In/trip module rating  ≤160  ≤250  ≤400 
Recommended Cable Sizes for IEC
DANGER 

hazard of electric shock, explosion, or arc flash
Failure to follow these instructions will result in death or serious injury.

The maximum number of cable connections per busbar:

4 on input/output/bypass busbars

4 x 240 mm^{2} on input/output/bypass busbars

4 x 240 mm^{2} or 8 x 150 mm^{2} on DC+/DC busbars

8 on N busbar

16 on PE busbar
Cable sizes in this manual are based on the minimum requirements in table B.52.3 and table B.52.5 of IEC 60364552 with the following assertions*:

90 °C conductors

An ambient temperature of 30 °C

Use of copper or aluminum conductors

Installation method F

Single layer on a perforated cable tray
PE cable size is based on table 54.2 of IEC 60364454.
If the ambient temperature is greater than 30 °C, larger conductors are to be selected in accordance with the correction factors of the IEC.
The DC cables are sized for the kW rating at end of discharge voltage and not the upstream breaker in accordance with IEC 60364 433.3 Omission of devices for protection against overload.
Copper
Copper
UPS rating  300 kW  350 kW  

Voltage (V)  380  400  415  440  380  400  415  440 
Input phases (mm^{2})  1 x 240  1 x 240  1 x 240  1 x 240  2 x 120  2 x 120  2 x 120  1 x 240 
Input PE (mm^{2})  1 x 120  1 x 120  1 x 120  1 x 120  1 x 120  1 x 120  1 x 120  1 x 120 
Bypass/output phases (mm^{2})  1 x 240  1 x 185  1 x 185  1 x 185  1 x 240  1 x 240  1 x 240  1 x 240 
Bypass PE/output PE (mm^{2})  1 x 120  1 x 95  1 x 95  1 x 95  1 x 120  1 x 120  1 x 120  1 x 120 
Neutral (mm^{2})  1 x 240  1 x 185  1 x 185  1 x 185  1 x 240  1 x 240  1 x 240  1 x 240 
DC+/DC (mm^{2})  2 x 150  2 x 185  
DC PE (mm^{2})  1 x 150  1 x 185  
Inverter midpoint cable for 3wire parallel (mm^{2})  1 x 240  1 x 240  1 x 240  1 x 240  2 x 120  2 x 120  2 x 120  1 x 240 
Copper
UPS rating  400 kW  450 kW  500 kW  

Voltage (V)  380  400  415  440  380  400  415  440  380  400  415  440 
Input phases (mm^{2})  2 x 150  2 x 150  2 x 150  2 x 150  2 x 240  2 x 240  2 x 185  2 x 150  2 x 240  2 x 240  2 x 240  2 x 240 
Input PE (mm^{2})  1 x 150  1 x 150  1 x 150  1 x 150  1 x 240  1 x 240  1 x 185  1 x 150  1 x 240  1 x 240  1 x 240  1 x 240 
Bypass/output phases (mm^{2})  2 x 150  2 x 150  2 x 120  1 x 240  2 x 185  2 x 150  2 x 150  2 x 150  2 x 240  2 x 240  2 x 185  2 x 150 
Bypass PE/output PE (mm^{2})  1 x 150  1 x 150  1 x 120  1 x 120  1 x 185  1 x 150  1 x 150  1 x 150  1 x 240  1 x 240  1 x 185  1 x 150 
Neutral (mm^{2})  2 x 150  2 x 150  2 x 120  1 x 240  2 x 185  2 x 150  2 x 150  2 x 150  2 x 240  2 x 240  2 x 185  2 x 150 
DC+/DC (mm^{2})  2 x 240  3 x 150  3 x 185  
DC PE (mm^{2})  1 x 240  2 x 120  2 x 150  
Inverter midpoint cable for 3wire parallel (mm^{2})  2 x 150  2 x 150  2 x 150  2 x 150  2 x 240  2 x 240  2 x 185  2 x 150  2 x 240  2 x 240  2 x 240  2 x 240 
Aluminum
UPS rating  200 kW  250 kW  

Voltage (V)  380  400  415  440  380  400  415  440 
Input phases (mm^{2})  1 x 185  1 x 185  1 x 185  1 x 150  1 x 240  1 x 240  1 x 240  1 x 240 
Input PE (mm^{2})  1 x 95  1 x 95  1 x 95  1 x 95  1 x 120  1 x 120  1 x 120  1 x 120 
Bypass/output phases (mm^{2})  1 x 150  1 x 150  1 x 150  1 x 150  1 x 240  1 x 240  1 x 185  1 x 185 
Bypass PE/output PE (mm^{2})  1 x 95  1 x 95  1 x 95  1 x 95  1 x 120  1 x 120  1 x 95  1 x 95 
Neutral (mm^{2})  1 x 150  1 x 150  1 x 150  1 x 150  1 x 240  1 x 240  1 x 185  1 x 185 
DC+/DC (mm^{2})  2 x 120  2 x 150  
DC PE (mm^{2})  1 x 120  1 x 150  
Inverter midpoint cable for 3wire parallel (mm^{2})  1 x 185  1 x 185  1 x 185  1 x 150  1 x 240  1 x 240  1 x 240  1 x 240 
Aluminum
UPS rating  300 kW  350 kW  

Voltage (V)  380  400  415  440  380  400  415  440 
Input phases (mm^{2})  2 x 150  2 x 150  2 x 150  2 x 120  2 x 185  2 x 185  2 x 185  2 x 150 
Input PE (mm^{2})  1 x 150  1 x 150  1 x 150  1 x 120  1 x 185  1 x 185  1 x 185  1 x 150 
Bypass/output phases (mm^{2})  2 x 120  2 x 120  1 x 240  1 x 240  2 x 150  2 x 150  2 x 150  2 x 150 
Bypass PE/output PE (mm^{2})  1 x 120  1 x 120  1 x 120  1 x 120  1 x 150  1 x 150  1 x 150  1 x 150 
Neutral (mm^{2})  2 x 120  2 x 120  1 x 240  1 x 240  2 x 150  2 x 150  2 x 150  2 x 150 
DC+/DC (mm^{2})  2 x 240  3 x 150  
DC PE (mm^{2})  1 x 240  2 x 120  
Inverter midpoint cable for 3wire parallel (mm^{2})  2 x 150  2 x 150  2 x 150  2 x 120  2 x 185  2 x 185  2 x 185  2 x 150 
Aluminum
UPS rating  400 kW  450 kW  500 kW  

Voltage (V)  380  400  415  440  380  400  415  440  380  400  415  440 
Input phases (mm^{2})  2 x 240  2 x 240  2 x 240  2 x 240  (3 x 185)*  (3 x 185)*  2 x 240  2 x 240  (3 x 185)*  (3 x 185)*  (3 x 185)*  (3 x 185)* 
Input PE (mm^{2})  1 x 240  1 x 240  1 x 240  1 x 240  2 x 150  2 x 150  1 x 240  1 x 240  2 x 150  2 x 150  2 x 150  2 x 150 
Bypass/output phases (mm^{2})  2 x 240  2 x 240  2 x 185  2 x 150  2 x 240  2 x 240  2 x 240  2 x 240  (3 x 185)*  (3 x 185)*  2 x 240  2 x 240 
Bypass PE/output PE (mm^{2})  1 x 240  1 x 240  1 x 185  1 x 150  1 x 240  1 x 240  1 x 240  1 x 240  2 x 150  2 x 150  1 x 240  1 x 240 
Neutral (mm^{2})  2 x 240  2 x 240  2 x 185  2 x 150  2 x 240  2 x 240  2 x 240  2 x 240  (3 x 185)*  (3 x 185)*  2 x 240  2 x 240 
DC+/DC (mm^{2})  3 x 185  3 x 240  4x185  
DC PE (mm^{2})  2 x 150  2 x 185  2 x 185  
Inverter midpoint cable for 3wire parallel (mm^{2})  2 x 240  2 x 240  2 x 240  2 x 240  (3 x 185)  (3 x 185)  2 x 240  2 x 240  (3 x 185)  (3 x 185)  (3 x 185)  (3 x 185) 
Guidance for Organizing Input, Bypass, And Output Cables
The input, bypass, and output cables must be grouped in circuits. On raceways, use one of the two shown cable formations.
Load Sharing in Bypass Operation in a Parallel System
The impedance of the bypass paths need to be controlled in a parallel UPS system. When operating in bypass mode, the parallel load sharing is determined by the total impedance of the bypass path comprising cables, switchgear, static bypass switch, and cable formation.
NOTICE 

Risk of equipment damage
To ensure correct load sharing in bypass operation in a parallel system, the following
recommendations apply:
Failure to follow these instructions can result in equipment damage.

eConversion Limits for Parallel UPS Systems
eConversion requires a minimum load percentage on the UPS for parallel UPS systems. The minimum required load percentages depend on the power cable sizes.
Standard eConversion Limits Based on Recommended Cable Sizes
UPS rating  Minimum load % 

200 kW  34% 
250 kW  27% 
300 kW  23% 
350 kW  19% 
400 kW  17% 
450 kW  15% 
500 kW  14% 
The other prerequisites to use this table include:

The values are calculated based on the use of recommended cable sizes.

Installations with maximum two cables on each phase are supported.

The bypass and output cables must have equal length for all UPSs.
Standard eConversion Limits Based on Nonrecommended Cable Sizes
UPS rating  Minimum load % 

200 kW  50% 
250 kW  40% 
300 kW  34% 
350 kW  29% 
400 kW  25% 
450 kW  22% 
500 kW  20% 
The other prerequisites to use this table include:

The values are calculated based on the scenario of using nonrecommended cable sizes.

Installations with three or four cables on each phase are supported.

The bypass and output cables must have equal length for all UPSs.
For 3Wire Parallel Systems Only
In a parallel installation installed as a 3wire AC configuration, the inverter midpoint of each UPS must be interconnected by cable in a daisy chain configuration. The inverter midpoint cable size can be found in the recommended cable sizes table.
When the inverter midpoint of the parallel UPSs is permanently connected, there is still potentially dangerous voltage present on the neutral busbar inside the UPS even after the UPS has been isolated from the parallel system for maintenance and has been completely shut down. Due to the dangerous voltages on the neutral busbar, all service activities that need access inside the I/O section by opening the inner door require full shutdown of the entire parallel system and transfer to maintenance bypass.
DANGER 

Hazard of electric shock, explosion, or arc flash
Failure to follow these instructions will result in death or serious injury.

Torque Specifications
Bolt size  Torque 

M6  5 Nm 
M8  17.5 Nm 
M10  30 Nm 
M12  50 Nm 