hazard of electric shock, explosion or arc flash
Place the battery breaker box as close to the battery bank as possible to limit the length of unprotected battery cable. The distance between the battery bank and the UPS must not exceed 200 m. Contact Schneider Electric for installations with a longer distance.
Failure to follow these instructions will result in death or serious injury.
- Mount the Battery Breaker Box to the Wall.
- Prepare the Battery Breaker Box for Cables.
- Connect the signal cables. Perform one of the following procedures:
- Connect the Power Cables.
- Add Translated Safety Labels to Your Product.
- Final Installation Steps.