Connect Signal Cables for External Synchronization
- Remove the transparent protection cover from the external sync board 0P4809. The external sync board 0P4809 is located on the rear of the front plate.
- Connect the cables for external synchronization to the external sync board 0P4809 and to terminals J8309 and J8310. See cable routing on the illustration. Connect the external synchronization according to the diagram below that matches your UPS system.
- Reinstall the transparent protection cover on the external sync board 0P4809 after
signal cabling is completed.
DANGERHazard of electric shock, explosion, or arc flashThe transparent protection cover must be installed over the external sync board 0P4809.Failure to follow these instructions will result in death or serious injury.