Position the UPS
Hazard of electric shock, explosion, or arc flash
The UPS must be secured against movement. Perform one of the following once the UPS is in its final position:
Failure to follow these instructions will result in death or serious injury.
- Push the UPS into final position.
- Perform one of the following:
- Reinstall the front transportation bracket (870-32577) on the UPS and mount it to the floor. Use appropriate hardware for the floor type – the hole diameter in the bracket is ø14 mm. Minimum requirement is M12 strength grade 8.8 hardware.
- Lower the front and rear leveling feet on the UPS with a wrench until they connect
with the floor. The casters must not have contact with the floor. Use a bubble-leveler
to check that the UPS is level.
NOTICERisk of equipment damageDo not move the cabinet after the leveling feet have been lowered.Failure to follow these instructions can result in equipment damage. NOTICERisk of equipment damageIf leveling feet are used, the UPS may overheat because of the circulating hot air from the rear outlets. Be sure to install the front transportation bracket to block the backflow.Failure to follow these instructions can result in equipment damage.