Description of a Circuit Breaker with a 9422 Toggle Handle
Class 9422 Circuit Breaker Operating Mechanism
Class 9422 Circuit Breaker Operating Mechanisms are designed for installation in custom-built control enclosures where main or branch circuit protective devices are required. All circuit breaker operating mechanisms are suitable for either right- or left-hand flange mounting and are convertible on site.
Complete 9422 Kits
Complete kits are rated for NEMA Type 1, 3R and 12 enclosures, and a door-drilling template is supplied to ease installation. They include a handle assembly, operating mechanism, and shaft assembly.
Class 9422 Flexible Cable Operating Mechanisms
For tall, deep enclosures where placement flexibility is required, it is possible to use a flexible cable operating mechanism with the Class 9422Ax handle for the PowerPact B-frame circuit breaker.
PowerPact B Front Face with 9422 Toggle Handle
The controls, indicators, and locking mechanism are located as follows:
The operating control is on the enclosure.
The operation indicators are on the circuit breaker and on the handle operator.
The locking mechanism is on the handle operator.
The following figure shows the Class 9422 operating mechanism and a Class 9422 operating mechanism
with a flange-mounted toggle handle. The handle is sold separately
Device Identification for PowerPact B with 9422 Toggle Handle
Information about the circuit breaker is given on the device identification label(see Description of a Circuit Breaker with a Direct Rotary Handle).
Scan the QR code to get additional information about the circuit breaker from the Schneider Electric web site. To scan the QR code, use a smartphone that is equipped with a camera and installed with a QR code reader.