Isolate a Single UPS from the Parallel System
Use this procedure to shut down one UPS in a running parallel system.
- On the display select and then select confirm to power off the UPS.
- Turn the battery breaker(s) BB of the UPS to the OFF (open) position.
- Turn the mains input breaker MIB of the UPS to the OFF (open) position.
- Turn the bypass input breaker BIB of the UPS to the OFF (open) position.
- Turn the external unit output breaker Ext. UOB of the UPS to the OFF (open) position.
- For the UPS with internal batteries, disconnect all batteries
on the front of the UPS.
DANGERhazard of electrical shock, explosion or arc flash
Failure to follow these instructions will result in death or serious injury.
- Wait at least 5 minutes before removing the cover of the UPS after the display has turned off to allow for the capacitors to fully discharged.
- Always measure for hazardous voltages on all terminals before working on the UPS.