Example application: Ungrounded power system insulation monitoring connected to a communication network
An ungrounded power system is a system involving the use of a transformer whose neutral is not connected to ground.
When the IMD is linked to the supervisor via a Modbus connection, the following actions are supported:
Display: The product status, the status of the insulation alarm (active, inactive, acknowledged), the status of the preventive insulation alarm, details of the last 30 time-tagged events, the values for R and C in order to create tables or curves for monitoring these values over variable periods
Configure the product remotely. All the settings can be accessed remotely, with the exception of the Modbus parameters.