Start Up the UPS System from Off Mode
- Close the unit input breaker UIB. The display turns on. The rebooting sequence lasts approximately 3 minutes.
- Close the static switch input breaker SSIB (if present).
- Close the battery breakers (if present).
- Close the unit output breaker UOB.
- Close the system isolation breaker SIB (if present).
- Turn on the inverter by pressing the inverter ON button on the controller box or by following Turn the Inverter ON.