Data display screens
The titles listed are for the HMI mode in IEEE, with the corresponding titles in IEC mode in square brackets [ ].

Bulleted items indicate subscreens and their descriptions.
Current
Amps [I]
Amps Per Phase  Instantaneous current measurements for each phase and neutral. 
Dmd

Summary of peak current demand values at the last demand interval.

Ig  Average (Iavg), neutral (In) and residual/ground (Ig) current 
Voltage
Volts [UV]
Voltage LL [U]  Linetoline voltage for each phase. 
Voltage LN [V]  Linetoneutral voltage for each phase. 
Harmonics
Harm
Harmonics %  Graphical representation of harmonics (as a percent of fundamental). 
V LL [U]

Linetoline voltage harmonics data: Numeric magnitude and angle for the fundamental harmonic, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each linetoline phase voltage. 
V LN [V]

Linetoneutral voltage harmonics data: Numeric magnitude and angle for the fundamental harmonic, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each linetoneutral phase voltage. 
Amps [I]

Current harmonics data: Numeric magnitude and angle for the fundamental harmonics, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each phase current. 
TDD  Total demand distortion each phase voltage. 
Power
Power [PQS]
Power Summary  Summary of realtime power consumption values for total active power in kW (Total [Ptot]), total reactive power in kVAR (Total [Qtot]), and total apparent power in kVA (Total [Stot]). 
Phase

Per phase (A [P1], B [P2], C [P3]) and total (Total [Ptot]) power values for active power in kW, reactive power in kVAR and apparent power in kVA. 
Pwr Dmd Summary

Summary of peak power demand values in the previous (Last) demand interval period for active power in kW, reactive power in kVAR and apparent power in kVA.

Energy
Energy [E]
Wh, VAh, VARh 
Delivered (Del), received (Rec), delivered plus received (D+R) and delivered minus received (DR) accumulated values for active energy (Wh), apparent energy (VAh) and reactive energy (VARh). 
Tariff


Power Factor
PF
True 
Per phase and total true power factor values and sign. 
Disp 
Per phase and total displacement power factor values and sign. 
Frequency
Hz [F]
Frequency (Freq), average voltage (Vavg), average current (Iavg) and total power factor (PF) values. 
Total harmonic distortion
THD
THD

THD (ratio of harmonic content to the fundamental) for current, linetoline voltage and linetoneutral voltage. 
thd

thd (ratio of harmonic content to the rms value of total harmonic content) for current, linetoline voltage and linetoneutral voltage. 
Unbalance
Unbal
Percent unbalance readings for linetoline voltage (V LL [U]), linetoneutral voltage (V LN [V]) and current (Amps [I]). 
Minimum / maximum
MnMx
Max Summary

Summary of maximum values for linetoline voltage, linetoneutral voltage, phase current and total power.

Power [PQS]

Minimum and maximum values for active, reactive, and apparent power. 
PF

Minimum and maximum values for true and displacement PF and PF sign. 
Hz [F] 
Minimum and maximum values for frequency. 
THD

Minimum and maximum values for total harmonic distortion (THD or thd).

Unbal

Minimum and maximum values for current unbalance, linetoline voltage unbalance and linetoneutral voltage unbalance. 
Alarm
Alarm
Active, Hist, Count, Unack 
Lists all active alarms (Active), past alarms (Hist), the total number of times each standard alarm was tripped (Count), and all unacknowledged alarms (Unack). 
Input / output
I/O
D Out, S In, Relay 
Current status (on or off) of the selected digital output, status input or relay. Counter shows the total number of times an offtoon change of state is detected. Timer shows the total time (in seconds) that a digital output, status input or relay is in the on state. 
Timer
Timer
Load 
Realtime counter that keeps track of the total number of days, hours, minutes and seconds an active load is connected to the meter inputs. 
Oper 
Realtime counter for the total number of days, hours, minutes and seconds the meter has been powered. 
Maintenance
Maint
Reset 
Screens to perform global or single resets. 
Setup

Meter configuration screens. 
Diag

Diagnostic screens provide meter information, status and event data for troubleshooting. NonMID meter models : The Cl Pwr screen displays how many times the meter lost control power, and the date and time of its last occurrence. MID meter models : The Cl Pwr screen displays how many times the meter lost control power (auxiliary power), and the last power up and power down events with the timestamp. The PhAng screen displays a graphical representation of the power system the meter is monitoring. 
Clock
Clock
Meter date and time (local or GMT). 