Data display screens
The titles listed are for the HMI mode in IEEE, with the corresponding titles in IEC mode in square brackets [ ].

Bulleted items indicate subscreens and their descriptions.
Amps [I]
Amps [I] 
Instantaneous current measurements for each phase and calculated neutral (In) or calculated ground current (Ig) based on the meter wiring type. 
Dmd 
Summary of peak current demand values at the last demand interval. 




Volts [UV]
V LL [U] 
Linetoline voltage for each phase. 
V LN [V] 
Linetoneutral voltage for each phase. 
Power [PQS]
Power [PQS] 
Summary of realtime power consumption values for total active power in kW (Total [Ptot]), total reactive power in kVAR (Total [Qtot]), and total apparent power in kVA (Total [Stot]). 
Phase

Per phase (A [P1], B [P2], C [P3]) and total (Total [Ptot]) power values for active power in kW, reactive power in kVAR and apparent power in kVA. 
Dmd 
Summary of peak power demand values in the previous (Last) demand interval period for active power in kW, reactive power in kVAR and apparent power in kVA. 




Energy [E]
Wh, VAh, VARh 
Delivered (Del), received (Rec), delivered plus received (D+R) and delivered minus received (DR) accumulated values for active energy (Wh), apparent energy (VAh) and reactive energy (VARh). 
Tariff 



QR 
Energy parameters (Wh, VAh, VARh, and multitariff) embedded in QR code format. 
PF
True 
Per phase and total true power factor values and sign. 
Disp 
Per phase and total displacement power factor values and sign. 
Hz [F]
Frequency (Freq). This page also displays average voltage (Vavg), average current (Iavg) and total power factor (PF) values. 
THD
THD

THD (ratio of harmonic content to the fundamental) for current, linetoline voltage and linetoneutral voltage. 
thd

thd (ratio of harmonic content to the rms value of total harmonic content) for current, linetoline voltage and linetoneutral voltage. 
QR 
Power quality parameters (THD and thd) embedded in QR code format. 
Harm
V LL [U]

Linetoline voltage harmonics data: Numeric magnitude and angle for the fundamental harmonic, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each linetoline phase voltage. 
V LN [V]

Linetoneutral voltage harmonics data: Numeric magnitude and angle for the fundamental harmonic, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each linetoneutral phase voltage. 
Amps [I]

Current harmonics data: Numeric magnitude and angle for the fundamental harmonics, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each phase current. 
TDD 
Total demand distortion each phase voltage. 
Unbal
Percent unbalance readings for linetoline voltage (V LL [U]), linetoneutral voltage (V LN [V]) and current (Amps [I]). 
MnMx
Amps [I] 
Summary of minimum and maximum values for phase current. 
Volts [UV]

Summary of minimum and maximum values for linetoline voltage and linetoneutral voltage. 
Power [PQS]

Minimum and maximum values for active, reactive, and apparent power. 
PF

Minimum and maximum values for true and displacement PF and PF sign. 
Hz [F] 
Minimum and maximum values for frequency. 
THD 



Unbal

Minimum and maximum values for current unbalance, linetoline voltage unbalance and linetoneutral voltage unbalance. 
QR 
Minimum and maximum values (phase current, linetoline voltage, linetoneutral voltage, power (PQS), PF, frequency, power quality and Unbal) embedded in QR code format. 
Alarm
Active, Hist, Count, Unack 
Lists all active alarms (Active), past alarms (Hist), the total number of times each standard alarm was tripped (Count), and all unacknowledged alarms (Unack). 
QR 
Alarm parameters (active, past alarms, the total number of times each standard alarm was tripped, unacknowledged) embedded in QR code format. 
I/O
D Out
S In
Relay (PM5330 / PM5331 / PM5340 / PM5341 only)

Current status (on or off) of the selected digital output, status input or relay output. Counter shows the total number of times an offtoon change of state is detected. Timer shows the total time (in seconds) that a digital output, status input or relay is in the on state. 
Timer
Load 
Realtime counter that keeps track of the total number of days, hours, minutes and seconds an active load is connected to the meter inputs. 
Oper 
Realtime counter for the total number of days, hours, minutes and seconds the meter has been powered. 
QR
Meter info details, energy parameters, power demand parameters, basic parameter values (current, voltage and power), power quality parameters, minimum / maximum values (phase current, linetoline voltage, linetoneutral voltage, power (PQS), PF, frequency, power quality and Unbal), alarm parameters and data log parameters embedded in QR code format. 
Maint
Reset 
Screens to perform global or single resets. 
Setup 













Diag 
Diagnostic screens provide meter information, status and event data for troubleshooting. 










Clock
Meter date and time (local or GMT). 