Setting up alarms using the display
It is recommended that you use ION Setup to configure standard (1-Sec) alarms. ION Setup supports a higher resolution to allow you to specify more decimal places when setting up the pickup setpoint and dropout setpoint values for certain measurements.
- Navigate to the alarms setup menu screens and select the alarm you want to set up.
- Configure the setup parameters as explained in the different
alarm setup sections.NOTE: If you used ION Setup to program decimal values on a standard (1-Sec) alarm, do not use the meter display to make subsequent changes to any alarm parameters (including enable/disable), as doing so will cause removal of all decimals previously programmed through ION Setup.
- Click Yes to save the changes to the meter when prompted.