The peak for each value is the highest average reading since the meter was last reset. These values are maintained in the meter’s non-volatile memory.
The meter also stores the date and time when the peak demand occurred. In addition to the peak demand, the meter also stores the coinciding average 3-phase power factor. The average 3-phase power factor is defined as “demand kW/demand kVA” for the peak demand interval.