Data display screens
The titles listed are for the HMI mode in IEEE, with the corresponding titles in IEC mode in square brackets [ ].

Bulleted items indicate subscreens and their descriptions.
Current
Amps [I]
Amps Per Phase  Instantaneous current measurements for each phase and neutral (Ia [I1], Ib [I2], Ic [I3], In). 
Dmd 
Summary of peak current demand values at the last demand interval for each phase and neutral (Ia [I1], Ib [I2], Ic [I3], In). 




Ig  Average (Iavg), neutral (In) and residual/ground (Ig) current. 
RCM (PM5660 / PM5661 / PM5760 / PM5761 only)  Instantaneous residual current measurement (I5 and I6). 
Voltage
Volts [UV]
Voltage LL [U]  Linetoline phase voltage (Vab [U12], Vbc [U23], Vca [U31]). 
Voltage LN [V]  Linetoneutral phase voltage (Van [V1], Vbn [V2]), Vcn [V3]). 
Harmonics
Harm
Harmonics %  Graphical representation of harmonics (as a percent of fundamental). 
V LL [U]

Linetoline voltage harmonics data: Numeric magnitude and angle for the fundamental harmonic, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each linetoline phase voltage (Vab [U12], Vbc [U23], Vca [U31]). 
V LN [V]

Linetoneutral voltage harmonics data: Numeric magnitude and angle for the fundamental harmonic, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each linetoneutral phase voltage (Van [V1], Vbn [V2]), Vcn [V3]). 
Amps [I]

Current harmonics data: Numeric magnitude and angle for the fundamental harmonics, and graphical representation of harmonics for the 3rd to 11th, 13th to 21st, and 23rd to 31st odd harmonics for each phase current (Ia [I1], Ib [I2], Ic [I3]). 
TDD/K  Total demand distortion and Kfactor data for each phase voltage (KF A [KF 1], KF B [KF 2], KF C [KF 3]). 
Crest

Crest factor data for each phase current (Ia [I1], Ib [I2], Ic [I3]), linetoline phase voltage (Vab [U12], Vbc [U23], Vca [U31]), and linetoneutral phase voltage (Van [V1], Vbn [V2]), Vcn [V3]). 
Power
Power [PQS]
Power Summary  Summary of realtime power consumption values for total active power in kW (Total [Ptot]), total reactive power in kVAR (Total [Qtot]), and total apparent power in kVA (Total [Stot]). 
Phase

Per phase and total power values for active power in kW (A [P1], B [P2], C [P3], Total [Ptot]), reactive power in kVAR (A [Q1], B [Q2], C [Q3], Total [Qtot]) and apparent power in kVA (A [S1], B [S2], C [S3], Total [Stot]). 
Pwr Dmd Summary 
Summary of peak power demand values in the previous (Last) demand interval period for active power in kW, reactive power in kVAR and apparent power in kVA. 








Energy
Energy [E]
Wh, VAh, VARh 
Delivered (Del), received (Rec), delivered plus received (D+R) and delivered minus received (DR) accumulated values for active energy (Wh), apparent energy (VAh) and reactive energy (VARh). 
Tariff 









Inp Mtr 
Accumulated values on the input metering channels (Ch 1 to Ch 4). 






QR 
Energy parameters (Wh, VAh, VARh, Tariff and Input metering) embedded in QR code format. 
Power Factor
PF
True 
True power factor values per phase and total (PFa [PF1], PFb [PF2], PFc [PF3], Total [Ptot]), PF sign, and load type (capacitive = lead, inductive = lag). 
Disp 
Displacement power factor values per phase and total (PFa [PF1], PFb [PF2], PFc [PF3], Total [Ptot]), PF sign, and load type (capacitive = lead, inductive = lag). 
Frequency
Hz [F]
Frequency (Freq), average voltage (Vavg), average current (Iavg) and total power factor (PF) values. 
Total harmonic distortion
THD
THD

THD (ratio of harmonic content to the fundamental) for phase currents (Ia [I1], Ib [I2], Ic [I3], In), linetoline voltages(Vab [U12], Vbc [U23], Vca [U31]) and linetoneutral voltages (Van [V1], Vbn [V2], Vcn [V3]). 
thd

thd (ratio of harmonic content to the rms value of total harmonic content) phase currents (Ia [I1], Ib [I2], Ic [I3], In), linetoline voltages(Vab [U12], Vbc [U23], Vca [U31]) and linetoneutral voltages (Van [V1], Vbn [V2], Vcn [V3]). 
QR 
Power quality parameters (THD and thd) embedded in QR code format. 
Unbalance
Unbal
Percent unbalance readings for linetoline voltage (V LL [U]), linetoneutral voltage (V LN [V]) and current (Amps [I]). 
Minimum / maximum
MnMx
MnMx

Summary of maximum values for linetoline voltage, linetoneutral voltage, phase current and total power.

Power [PQS]

Minimum and maximum values for active, reactive, and apparent power. 
PF

Minimum and maximum values for true and displacement PF and PF sign. 
Hz [F] 
Minimum and maximum values for frequency. 
THD

Minimum and maximum values for total harmonic distortion (THD or thd).

Unbal

Minimum and maximum values for current unbalance, linetoline voltage unbalance and linetoneutral voltage unbalance. 
QR 
Minimum and maximum values (phase current, linetoline voltage, linetoneutral voltage, power (PQS), PF, frequency, power quality and Unbal) embedded in QR code format. 
Alarm
Alarm
Active, Hist, Count, Unack 
Lists all active alarms (Active), past alarms (Hist), the total number of times each standard alarm was tripped (Count), and all unacknowledged alarms (Unack). 
QR 
Alarm parameters (active, past alarms, the total number of times each standard alarm was tripped, unacknowledged) embedded in QR code format. 
Input / Output
I/O
D Out, D In
A In (PM5570 only)

Current status (on or off) of the selected digital output or digital input. Counter shows the total number of times an offtoon change of state is detected. Timer shows the total time (in seconds) that a digital input or digital output is in the on state. Summary of analog inputs (A1 & A2).

Timer
Timer
Load 
Realtime counter that keeps track of the total number of days, hours, minutes and seconds an active load is connected to the meter inputs. 
Oper 
Realtime counter for the total number of days, hours, minutes and seconds the meter has been powered. 
QR
QR
QR 
Meter info details, energy parameters, power demand parameters, basic parameter values (current, voltage and power), power quality parameters, minimum / maximum values (phase current, linetoline voltage, linetoneutral voltage, power (PQS), PF, frequency, power quality and Unbal), alarm parameters and data log parameters embedded in QR code format. 
Maintenance
Maint
Reset 
Screens to perform global or single resets. 
Setup 



















Diag 
Diagnostic screens provide meter information for troubleshooting. 










Lock (PM5561 / PM5661 / PM5761 only)  This locks or unlocks the MID protected quantities. 
Clock
Clock
Meter date and time (local or GMT). 